Check more pictures about TurbineKey™ Gearbox Replacement & Alignment for GDF SUEZ Canada
* click images to see fullsize.
GDF Suez and Siemens Energy needed to replace their existing gearbox with a higher rated Flender-Graffenstaden gearbox to accommodate the turbine upgraded capacity. The new gearbox had a different shaft elevation and thermal signature so the original gearbox alignment position and target were no longer relevant. GDF Suez and Siemens energy needed a way to swap out the gearbox in a compressed outage duration and receive an OEM warranty on the new gearbox and alignment. As a result, Siemens decided that the TurbineKey service provided by ACQUIP and FGGS was the best solution for this case.
The TurbineKey Engineers through ACQUIP and FGGS, were brought in to replace the gearbox. As found alignment readings were recorded on the original gearbox. The original gearbox was pulled out and the new gearbox was installed. The new alignment targets were calculated for the upgraded Flender Graffenstaden gearbox. The gearbox was aligned to the turbine and generator. FGGS engineers then ensured that the gearbox was leveled and proper contact was maintained between the gears.
The turbine was started without incidence. The Turbine was able to deliver full rated capacity to the Generator with the new gearbox. The vibration levels and temperatures of the new Flender-Graffenstaden Gearbox bearings were much lower than on the original gearbox.
Siemens and GDF Suez services, products and company names are trademarks™ or registered® trademarks of their respective holders. Use of them does not imply any affiliation with or endorsement by them. Siemens is a trademark of Siemens AG. GDF Suez is a trademark of GDF Suez.